- NEW AIR CONDITIONING SYSTEM:
- New centralized chilled water air conditioning system:
- Centralized Chilled Water Chillers - Three brand new chiller units,
YORK brand, 400TR, 3 phase, 480 Volts. Two (2) Chillers are capable
of providing the FULL air conditioning requirement of the building.
The third chiller is for "stand by". The AlC chiller is
utilizing the "OZONE friendly refrigerant - R134A.
- Cooling Towers - Three (3) matching brand new Baltimore cooling
tower model no. 15425 were installed with the chillers.
- Condenser and Chilled Water pumps- Three brand new ITT BELL&GOSSETT
horizontal split case (chilled water) 960gpm and end suction centrifugal
pumps (condenser water) 1200gpm were installed.
- Fan Coil Units (FCU) - Three hundred sixty three (363) brand new
FCU were installed in the building
- New Direct Expansion Air Conditioning System:
- Ballroom - Two (2) brand new 45TR each
- Satellite- One 30TR unit
- Lobby Extension - Four brand new 30TR each
- NEW ELECTRICITY SYSTEM:
- City Power - 2500KVA transformer. Primary volt at 34,500 volts dropped
to 480 volts, 3 phase with 3,200 ampere main breaker.
- Alternate City Power- 300amperecapacity,480volts,3 phase.
- Emergency Power Generator- Two(2) units 312KV A each, power generator,
with Cummins engine prime mover
- Emergency Power Generator - One(1) unit 1250KV A power generator
with Cummins engine prime mover.
- NEW SANITATION SYSTEM
- The hotel building has one sewer line and a separate drainage line.
Wastes in the building are direct throw to the City Sewer Line. Manila
City has it's own sewer line.
- NEW COMMUNICATION SYSTEM:
- The hotel has a brand new system of PABX as follows:
|NEC NEAX7400 ICS Model 140 (dual CPU) with HOTEL PACKAGE
|48|| ||lines C.O. lines
|8|| ||lines D.I.D. lines
|48|| ||lines Digital lines
|416|| ||lines DTMF lines
|4|| ||channels 4DAT
|3|| ||sets Operator Console
|20|| ||sets NEC Dterm 16DC Digital Terminal
|8|| ||sets NEC Dterm 8 digital terminal
|1|| ||lot Maintenance Administrative Terminal
|1|| ||lot Rectifier - Battery for 8 hours
|400|| ||units Telematrix 2700 MS5
|400|| ||units Bathroom Telephone RS605T
|1|| ||unit Call Accounting Software CAS-Hotel Application
- NEW INTERNAL TRANSPORT SYSTEM:
- Passenger Elevators - Three(3) units OTIS elevator, completely rehabilitated,
basement to 12th floor.
- Service Elevator - One (1) unit OTIS brand new, basement to 10th
- Escalator- Two (2) units brand new Hitachi escalators
- Dumb Waiter - Two (2) units brand new Hitachi dumb waiter
- NEW FIRE AND SAFETY SYSTEM:
- The building is 100% completely covered with upright and pendant type
- The building has ample Fire Hose cabinets.
- The building has three separate Fire Stair Wells for fire escape.
- The Jockey pump and Fire pump are operational.
- The hotel has built-in Fire alarm and detection system.
- The hotel has a fife tank with 26,000 gallons of water capacity.
- NEW EXPANDED COMFORT ROOMS:
- New wash basin
- New water closet
- New bath tub
- NEW FURNITURES, FIXTURES AND CARPETS IN ALL GUESTROOM
- NEW TABLES AND CHAIRS IN ALL RESTAURANTS AND FUNCTION ROOMS
- NEW EQUIPTMENT IN ALL RESTAURANTS AND KITCHENS